CALL US - WE CAN BUILD IT!
By Part Number
Heatrex custom manufactures
TUBULAR & FINNED TUBULAR
HEATING ELEMENTS, IMMERSION
HEATERS, DUCT HEATERS,
UNIT HEATERS & CIRCULATION
Tubular & Finned Tubular
Process Duct Heaters
HVAC Electric Duct
Unit and Comfort Heaters
P.O. Box 515,
Meadville, PA 16335
Phone: (814) 724-1800
Fax: (814) 333-6580
HVAC Electric Duct Heaters
Email This Page
Save To Favorites
Finned Tubular HVAC Duct Heater
A job specification can be prepared by using the following information. Simply darken the applicable circles. Material which is part of the basic specification has already been darkened. Additional copies of this specification guide are available from your local Heatrex representative.
Duct heaters shall be Heatrex:
Type TFHU Standard Slip-in heaters.
Approvals - Heaters and panelboards (if required) shall meet the requirements of the National Electrical Code and shall be listed by Underwriters Laboratories for zero clearance to combustible surfaces and for use with heat pumps and air conditioning equipment.
Heating elements shall consist of a coil, 80% nickel, 20% chromium, Grade A resistance wire, precisely centered in a stainless steel tube filled with granular magnesium oxide. A stainless steel fin is to be helically wound onto the tube. Elements are to be furnished with mounting flanges, making them individually removable through the terminal box.
Heater frames and terminal boxes shall be corrosion resistant steel. Unless otherwise indicated, the terminal box shall be NEMA 1 construction and shall be provided with a hinged, latching cover and multiple concentric knockouts for field wiring.
All heaters shall be furnished with triple over temperature protection. A disc type and linear, automatic reset thermal cutout are included for primary over temperature protection. All heaters must also be furnished with a linear type manual reset thermal cutout with backup contactors (as required). For secondary over temperature protection, heat limiters or other fusible over temperature devices are not acceptable.
Heaters shall be rated for the voltage, phase and number of heating stages indicated in the schedule. All three-phase heaters shall have equal, balanced, three-phase stages. All internal wiring shall be stranded copper with 105°C insulation and shall be terminated in crimped connectors or box lugs.
Terminal blocks shall be provided for all field wiring and shall be sized for installation of 75°C copper wire rated in accordance with NEC requirements.
Heaters shall be furnished either with the Control Option specified in the schedule and described below or with the specific components listed in the schedule.
Non UL listed
TFHU (standard slip-in)
Control G (contactor control)
Control J (pneumatic control)
Control K (SCR control)
Disconnecting Contactors (substitute for De-Energizing Contactors)
Dust-tight Terminal Box
Fan Relay (in addition to Airflow Switch)
Fan Relay (substitute for Airflow Switch)
Insulated Terminal Box
Mercury Contactors (substitute for De-Energizing Contactors, not available in all areas)
Pilot Lights "Heater On"
Pilot Lights "Low Airflow"
Pilot Lights "Stage On"
HVAC Electric Duct Heaters Dimensional Drawing - Finned Tubular
HVAC Electric Duct Heaters Design Specifications
HVAC Electric Duct Heaters Specific Requirements
HVAC Electric Duct Heaters Installation Information
HVAC Electric Duct Heaters Electrical Construction
HVAC Electric Duct Heaters Mechanical Construction
HVAC Electric Duct Heaters Troubleshooting Guide
HVAC Electric Duct Heaters Slip and Drive Construction
Special Feature Codes - Finned Tubular
Replacement Parts Order Form
Electric Duct Heaters IOM
Site created by
ThomasNet Web Solutions
and powered by